An assessment of moisture induced damage in Blickling Hall in Norfolk, England, via environmental monitoring
© The Author(s) 2017
Received: 12 November 2016
Accepted: 17 January 2017
Published: 30 January 2017
In the last few decades, extreme weather events mostly characterized by more intense and frequent precipitation and wind incidents have risen, and current climatic projections strongly suggest that this trend will keep its pace in the future. These climatic conditions pose additional hygrothermal loading onto the built environment, which may lead to moisture induced deterioration and even strength reduction in masonry. Despite their already long service lives, this impact may in time become problematic for historic buildings, which, by nature of their design and construction, interact with moisture and climate to a far greater degree than modern buildings. The PARNASSUS project was set up with the aim of identifying and quantifying the impact of environment on historic buildings in the face of a changing climate. As part of this project, an extensive environmental monitoring campaign was carried out between 2012 and 2014 at Blicking Hall, a National Trust property in Norfolk, England, with the aim of providing further insight into the building’s overall performance under hygrothermal loading. Environmental monitoring work targeted not only indoor and outdoor conditions, but provided information about the temperature and relative humidity profiles across the walls by means of in-wall probes. Wind and rain gauges helped quantify other environmental parameters. This paper presents the findings from this environmental monitoring work, with specific emphasis on the basement suffering from sustained saturation in vapour phase and resulting biological growth, as well as the Long Gallery, where Blickling’s valuable library is kept.
KeywordsEnvironmental monitoring Moisture-induced damage Wind-driven rain Mould Condensation
Despite high local variations and associated uncertainties, current trends show that significant changes are taking place in the global climate . UK is among the European countries suffering most from this impact in various ways . It is expected that seasonal temperatures, and precipitation and wind patterns will dramatically change in the course of coming decades, which will bring along more frequent and intense extreme weather events. The total amount of rainfall is expected to increase in winter [3, 4] and, to a lesser extent, in spring and autumn, but this increase does not always accompany an increase in the number of wet days, which may result in more intense rainfall events that might, in turn, trigger both urban and riverine flooding . These observations are in broad agreement with the conclusions drawn by Jones and Reid  with regard to expected heavy precipitation events in the UK. It is a well-established fact that the resulting moisture loading, both cyclical and sustained loading, have a wide variety of implications ranging from issues such as mould formation or other biodeterioration, to those that may in time jeopardize the material and structural integrity of built environment such as material erosion, and loss of strength and stiffness (e.g. [7–11]).
Blickling Hall is one of the most famous Jacobean mansions, dating from the early seventeenth century and known for its outstanding architectural features . The building has a double courtyard plan, with a great hall in between . It is a Grade I listed property located in a registered park of total area 340 ha, near Aylsham in Norfolk, England . Blickling Hall was given to the National Trust in 1940 under the terms of the 1937 Country Houses Scheme . The locality is under constant threat of flooding of the River Bure basin, the most famous one being the big 1912 Norwich flood. More recently, Blickling has been affected by pluvial flooding, in September 2001, August 2004, June 2007, September 2008 and August 2014. Furthermore, the building is known to have high exposure to wind-driven rain and freezing conditions during winter .
The building is generally in a good state of preservation, however the lower elevations, especially the basement area is clearly affected by sustained high levels of moisture due to saturated soil below the basement window level, leading to biological growth and salt crystallization. Maurice Adams, as early as 1894, describes the continually saturated basement walls due to non-functional drains from a faulty culvert extending on the sides of the building on almost the same level as the basement, and mentions that it even often partly fills up the basement with sewer-contaminated water and that “the walls were green with damp”. Adams in 1894  gives a full account of the replacement of the hugely deteriorated culvert with a pipe system, and although there is no mention of that in this paper, the tanking that is currently present within the basement is thought to have been built towards the end of the nineteenth century, perhaps also by Adams himself. In the early 2000s more interventions took place to further improve the drainage issues of this space, which included cleaning and repairing the historic brick rainwater culvert which extends around the perimeter of the mansion and to address surface water management and run off issues in the upper front meadows inundating the front forecourt of the house. Following these maintenance improvements there has been little to no occurrences of major flooding in the basements or within the dry moat.
On its eastern side the Hall contains one of the most significant libraries in the National Trust, filled with Sir Richard Ellys’s books . Ellys’s library was installed in 1745 in the Long Gallery , one of the finest rooms at Blickling with its elaborately decorated Jacobean plaster ceiling, has been the principle focus for content conservation for some years within the house. The library is known to suffer on and off from mould growth on leather and vellum book bindings, notably at the back of the books, where temperature may be lower due to radiant heat loss from the external walls. In the 1980s, the presses were altered by extending the depth of the shelves so that ventilation holes could be drilled at the back of the shelves to facilitate ventilation behind the book stack and mitigate mould growth. However, occasional mould growth still occurs. Another significant issue within the library is deathwatch beetle infestation, of the textblock of books and wooden structural elements, especially at the North end of the library. This may be related to poor environmental conditions inside the library at this time, as well as past water ingress, such as flooding caused by failure of rainwater goods that was discovered in 1999. Water-soaked or decayed timber is vulnerable to insect attack [19–21]. Since these events, the National Trust has made considerable effort to prevent water ingress through repair and maintenance of the building fabric and rainwater goods. In the Long Gallery itself heating is used to prevent high humidity conditions that can encourage mould growth and insect infestation, aiming to keep indoor relative humidity level below about 60%. The North East Turret is also subject to death watch beetle infestation, due to a long history of water ingress affecting its timbers. For all these reasons, with the aim of identifying and quantifying the environmental exposure, Blickling Hall was monitored between August 2012 and October 2014 using an extensive monitoring system, which is described in detail below. This paper summarizes the findings of this monitoring study and discusses the susceptibility of the building envelope to moisture-induced damage.
Sensors used in the monitoring of Blickling Hall and their specifications
Speed and direction range: 0–60 m/s and 0–359°
Speed and direction accuracy: ±2% and ± 3°
Speed and direction resolution: 0.01 m/s and 1°
Wind direction range: 0–359° (no dead band)
Wind direction accuracy: ±3° @12 m/s
Wind direction resolution: 1°
Horizontal rainfall (HRF) gauge
Tipping bucket rain gauge with resolution of 1 pulse equal to 0.1 mm
Wind-driven rain gauges
Outdoor temperature and RH sensor
−50 to +100 °C for temperature; accuracy ±0.1 °C
0–100% for RH; accuracy ±0.8%
In-wall temperature and relative humidity probes
−40 to +100 °C for temperature; accuracy ±0.1 °C
0–100% for RH; accuracy ±0.8%
Indoor temperature and RH sensor
−40 °C to +120 °C for temperature; accuracy ± 0.5 °C
0–100% for RH; accuracy ±1.5%
Maximum operating temperature of +350 °C, shielded against solar radiation
Water height sensor
Optimum range: 20.3 cm to 4.0 m
Maximum range: 6.1 m
Resolution: 0.344 mm
Separately, a set of standalone temperature and relative humidity sensors (EL-USB-2) were placed in various places across the building (in the basement for in-wall indoor values, in the gallery for in-wall values and underneath a moat in the garden for outdoor values) to monitor the temperature and relative humidity (measurement ranges: 0–100% RH±, −35 to +80 °C T ± 0.5 °C), again on a half-hourly basis. These standalone sensors were chosen from the thinnest products available commercially (around 2 cm thickness) to ensure limited impact on historic fabric, and disruption to mortar joints. Existing cracks or other defects on the walls were exploited for their placement in order to minimize intervention. In addition, the National Trust’s outdoor and gallery indoors monitoring data were used in this paper.
The obtained results are discussed in the following sections in relation to the likelihood of most common moisture-induced damaging mechanisms in various sections of Blickling Hall.
Impact of temperature and relative humidity variations
The Long Gallery where the library of Blickling Hall is kept is one of the highlights of the entire property. This study therefore included the in-wall monitoring of the Long Gallery. The results show that the gallery in-wall temperatures fluctuate between 5.5 and 25 °C with an average of 14.4 °C, while the relative humidity values vary between 66.5 and 77% with an average of 72%. The fact that the in-wall relative humidity values are all lower than 77% is quite positive from a biodeterioration point of view and an indication that the building fabric is coping well with the local climate. The rarity of wind incidents with speeds higher than 2 m/s are considered to contribute to the relatively low in-wall relative humidity values (discussed more in depth in “In-wall moisture enrichment due to rain penetration” section). When the daily maximum variations are examined, one sees that the maximum daily difference in the relative humidity values is in the range of 12%, whilst this is negligible for temperature values. The likely implications of these high relative humidity values combined with temperatures at the high end is further discussed in “Mould formation and other moisture induced bio-deterioration” section. Also, it is noteworthy that even when the outdoor temperature values fall below the freezing point, the in-wall temperatures stay above 0 °C. In fact, the minimum in-wall temperature is 5.5 °C. Therefore, cyclic freeze and thaw is not a relevant phenomenon for this part of the estate.
In-wall moisture enrichment due to rain penetration
We also see that the inner and outer wall surface temperature peaks and troughs happen at the same time, suggesting low thermal inertia once again. The in-wall temperature values on the other hand are rather constant. We also see that the peaks in the in-wall RH values correspond to peaks in the outer surface temperatures, pointing out presence of free water within the building fabric.
As mentioned in “Impact of temperature and relative humidity variations” section, the gallery in-wall relative humidity values are always below 77%, which, compared to the in-wall RH values measured in the unheated turret attached to the North East corner of the Long Gallery, are quite low. On this particular wall, we do not observe a similar moisture enrichment phenomenon, even under heavy rain incidents that satisfies the half-day with more than 4 mm of horizontal rainfall criterion. This is considered to be due to the fact that the wall is not facing the prevalent wind direction and is not exposed to wind speeds higher than 2 m/s.
Mould formation and other moisture induced bio-deterioration
Mould is known to occur in highly humid environments, including, notably, confined indoor spaces. In addition to surrounding environmental conditions, the type, surface texture and cleanliness of the substrate, as well as incubation duration and amount and type of available light are known to influence the likelihood of mould growth . Despite the abundance of studies focusing on benchmarking of minimum temperature and humidity conditions that may result in an onset of mould formation on different building materials (e.g. [26–28]), different values were reported for the minimum RH values that govern and possibly trigger the onset of the mould growth, if no other information is available: 70% , 75% [28, 30], and 80% . As the relative humidity increases, the temperature that should accompany it for an onset of mould growth decreases. However, the temperature interval optimal for the germination of most species is roughly 15–30 °C , which covers common temperature levels in controlled or uncontrolled indoor environments, but depending on the humidity conditions it can be as low as 10 °C, although that would significantly reduce the growing rate .
As mentioned in “Environmental monitoring” section, a structural timber component embedded within an attic wall above the Long Gallery (purple dot in Fig. 1) was included within the monitoring programme. The same exercise using the monitoring results obtained here, shows that the timber element is quite vulnerable to mould growth, especially in winter and springtime. More concerning, is that the timber is likely to have as a consequence, high equilibrium moisture content enabling death watch beetle larvae to consume the wood. Death watch beetle attack has been observed in various timbers in Blickling, notably in the upper levels of the North East Turret. Fisher  states that the level of existing decay in the wood attacked by the deathwatch is another important factor—the more decayed the timber the more prone it is to be attacked. Also, fungi-infested timber is more suitable for the development of these insects.
The data obtained from the basement show that the in-wall temperature values are equal to or lower than the calculated dew point temperature for more than 70% of the time. Moreover, the data shows that most of these incidents take place in relatively warm months, i.e. from May to October. Therefore, one can conclude that interstitial condensation is a serious risk factor for the basement, especially in summer and autumn.
Another location that seems to suffer from occasional condensation is the North East Turret. An analysis of the temperature and relative humidity values show that the temperature values are lower than the dew point for almost a quarter of all readings. Here, on the other hand, the critical season seems to be the winter. The times of the year where condensation occurs in these two different parts of the building are completely different, which can be attributed to different phenomena triggering condensation: summer condensation is commonly seen in historic buildings with very thick walls , especially in underground structures such as crypts (see ) and caves, and is an indication of relatively warmer surface temperatures, humid air and still cold building envelopes. Winter condensation, on the other hand, is rather a result of cold air surrounding the relatively warm building fabric. The fact that the basement is partly below ground level keeps the building fabric at quite low temperatures regardless of the season, whereas the monitored portion of the turret is quite high up and located very closely to the portion of the building that is frequently in use, and therefore the walls are relatively warmer.
Summary and conclusions
This paper presents the results obtained from a long monitoring campaign on Blickling Hall, carried out between August 2012 and October 2014. The results show that the building envelope has a rather rapid thermal and hygric response. Moisture enrichment due to rain penetration is a critical issue and can be exacerbated by empty mortar joints or otherwise damaged pointing, and under heavier precipitation expected as a result of changes observed in climate. Additionally, it is seen that different parts of the building suffer from different environmental phenomena, with varying implications.
Based on the results obtained in this study, the following recommendations are proposed: the facades that are exposed to high winds, specifically north and south facing walls, are expected to absorb considerable moisture during wind-driven rain spells, and therefore it is critical to maintain the wind and water tightness of these facades in the current and increasingly wetter future climates. This result confirms the value of the National Trust regime of regular inspection and maintenance of rainwater goods such as gutters, hoppers and downpipes and ensuring that pointing and detailing is in good order.
Conservation heating should be used in parts of the building housing sensitive collections, to reduce the indoor relative humidity levels and thus eliminate susceptibility to mould growth and other biodeterioration. It was observed that death watch beetle infestations die back if the wood moisture content is consistently below 12% . Work is ongoing, follow recommendations from the National Trust’s building consultants, to remove severely infested timbers and create a drier environment for other timbers through dealing with water penetration and ensuring adequate ventilation and in some cases using active dehumidification. In the Long Gallery conservation heating to maintain RH below 60% is used to reduce wood moisture content of the book presses and other timber elements below the critical 12% threshold.
The basement walls are continually saturated in the vapour phase, and do not dry out even during relatively dry and warm outdoor conditions. On the other hand, most of the pressing drainage issues have been dealt with in the early 2000s and the conditions are currently quite stable. As the basement is expected to have some level of dampness because it is partly located underground; as a result, does not house vulnerable collections, a very dry building fabric is not required here; however, the conditions should be kept under close surveillance in order to make sure that conditions do not worsen as the outdoor climatic conditions get more problematic as expected in the light of current trends.
This study shows that the on-site monitoring is a powerful tool for an in-depth appraisal of the environmental loading that buildings are actually exposed to as well as of the hygrothermal performance of the building envelope. To this end, an ad hoc monitoring system that brings together measurement tools for not only indoor and outdoor but also the in-wall conditions, as well as wind and rain in the close vicinity of the building is needed. Environmental monitoring should be an integrated component of condition assessment and should inform activities towards the retrofitting and conservation of historic buildings.
YDA wrote the manuscript. YDA and DD made the data analysis. NB and CC provided information about the history of the hall, and outlined the past and present problems, as well as past interventions that were used to contextualise the monitoring work reported here. DD, NB and CC helped to draft the manuscript with thorough discussions. All authors read and approved the final manuscript.
The authors are grateful for the invaluable support and assistance of the National Trust, and would like to especially thank Katy Lithgow, Paul Coleman and Louise Green for their help and advice throughout the project and during the development of this manuscript. The monitoring system that was used for the examination of Blickling Hall was designed and installed as part of Parnassus Project (AH/H032525, 2010-2014), funded by AHRC-EPSRC Science and Heritage Research Programme. Dr Aykut Erkal’s substantial contribution in the design and installation of this system is kindly acknowledged.
The authors declare that they have no competing interests.
Open AccessThis article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made. The Creative Commons Public Domain Dedication waiver (http://creativecommons.org/publicdomain/zero/1.0/) applies to the data made available in this article, unless otherwise stated.
- IPCC. Climate change 2014: impacts, adaptation and vulnerability. Cambridge: Cambridge University Press; 2014.Google Scholar
- Sanders CH, Phillipson MC. UK adaptation strategy and technical measures: the impacts of climate change on buildings. Build Res Inf. 2003;31(3–4):210–21.View ArticleGoogle Scholar
- Brimblecombe P. Refining climate change threats to heritage. J Instit Conserv. 2014;37(2):85–93.View ArticleGoogle Scholar
- Jenkins GJ, Perry MC, Prior MJ. The climate of the United Kingdom and recent trends. Exeter: Met Office Hadley Centre; 2008.Google Scholar
- Osborn T, Maraun D. Changing intensity of rainfall over Britain. Norwich: Climatic Research Unit; 2008 (Information Sheet No. 15).Google Scholar
- Jones PD, Reid PA. Assessing future changes in extreme precipitation over Britain using regional climate model integrations. Int J Climatol. 2001;21(11):1337–56.View ArticleGoogle Scholar
- Aktas YD, D’Ayala D, Erkal A, Stephenson V. Environmental performance assessment using monitoring and DVS testing. Proc Instit Civil Eng Eng Hist Herit. 2015;168(1):3–16.Google Scholar
- D’Ayala D, Aktas YD. Moisture dynamics in the masonry fabric of historic buildings subjected to wind-driven rain and flooding. Build Environ. 2016;104:208–20.View ArticleGoogle Scholar
- Drdácký MF. Flood damage to historic buildings and structures. J Perform Constr Facil. 2010;24(5):439–45.View ArticleGoogle Scholar
- Stephenson V, Aktas YD, D’Ayala D. Assessment of flood and wind driven rain impact on mechanical properties of historic brick masonry. Historical masonry. Lyngby: Proceedings of international RILEM conference: materials, systems and structures in civil engineering; 2016. p. 155–64.
- Witzany J, Cejka T, Zigler R. The effect of moisture on significant mechanical characteristics of masonry. Statybinės Konstrukcijos ir Technologijos. 2010;2(3):79–85.View ArticleGoogle Scholar
- Stanley-Millson C, Newman J. Blicklign Hall: the building of a Jacobean mansion. Archit Hist. 1986;29:1–42.View ArticleGoogle Scholar
- West S. An overlooked inventory for Blickling Hall, Norfolk. Libr Hist. 2003;19(2):143–5.View ArticleGoogle Scholar
- Historic England. Historic England listing. 2017. https://historicengland.org.uk/listing/the-list/list-entry/1000154.
- Wade Martins S. The conservation movement in Norfolk: a history. Woodbridge: The Boydell Press; 2015.Google Scholar
- Blades N. Mitigating damage due to floods and moisture to heritage: the National Trust perspective. 2013. http://www.ucl.ac.uk/parnassus/workshop/presentation_nigel_blades.
- Adams M. Blickling Hall, Norfolk: its drainage, water supply and other works. J R Inst Br Archit. 1894;1(6):157–66.Google Scholar
- Staniforth S. Management of the environment in libraries in historic houses. In: Managing Library and Archive Collections in Historic Buildings: Papers given at the National Preservation Office Annual Conference held 5th November 2002 at the British Library. London: National Preservation Office; 2002. p. 30–35.
- Fisher RC. Studies of the biology of the death-watch beetle, Xestobium Rufovillosum de G II. The habits of the adult with special reference to the factors affecting aviposition. Ann Appl Biol. 1938;25(1):155–80.View ArticleGoogle Scholar
- Fisher RC. Studies of the biology of the death-watch beetle, Xestobium Rufovillosum de G. III. Fundal decay in timber in relation to the occurrence and rate of development of the insect. Ann Appl Biol. 1940;27(4):545–57.View ArticleGoogle Scholar
- Jacob A. Composites offer help in the conservation of historic buildings. Reinf Plast. 2007;51(2):30–4.View ArticleGoogle Scholar
- Baker PH, Sanders C, Galbraith GH, McLean RC. Blickling Hall basement case study. In: Cassar M, Hawkings C, editors. Engineering historic futures: Stakeholders Dissemination and Scientific Research Report. London: Centre for Sustainable Heritage, UCL; 2007. p. 19–39.Google Scholar
- MetOffice. Eastern England: climate. 2015. http://www.metoffice.gov.uk/climate/uk/regional-climates/ee.
- BSI. BS EN ISO 15927-3 Hygrothermal performance of buildings—calculation and presentation of climatic data part 3: Calculation of a driving rain index for vertical surfaces from hourly wind and rain data. Brussels: CEN; 2009.Google Scholar
- Grant C, Hunter CA, Flannigan B, Bravery AF. The moisture requirements of moulds isolated from domestic dwellings. Int Biodeterior. 1989;25(4):259–84.View ArticleGoogle Scholar
- Johansson P. Rapport TVBH-3051: critical moisture conditions for mould growth on building materials. Lund: Lund University; 2012.Google Scholar
- Johansson P, Svensson T, Ekstrand-Tobin A. Validation of critical moisture conditions for mould growth on building materials. Build Environ. 2013;62:201–9.View ArticleGoogle Scholar
- Johansson P, Ekstrand-Tobin A, Bok G. An innovative test method for evaluating the critical moisture level for mould growth on building materials. Build Environ. 2014;81:404–9.View ArticleGoogle Scholar
- Leissner J, Kilian R, Kotova L, Jacob D, Mikolajewicz U, Broström T, Ashley-Smith J, Schellen HL, Martens M, van Schijndel J, Antretter F, Winkler M, Bertolin C, Camuffo D, Simeunovic G, Vyhlidal T. Climate for culture: assessing the impact of climate change on the future indoor climate in historic buildings using simulations. Heritage Science. 2015;3(38):1–15.Google Scholar
- Isaksson T, Thelandersson S, Ekstrand-Tobin A, Johansson P. Critical conditions for onset of mould growth under varying climate conditions. Build Environ. 2010;45:1712–21.View ArticleGoogle Scholar
- BSI. BS 5250: 2002 Code of practice for control of condensation in buildings. London: BSI; 2005.Google Scholar
- Pasanen A-L, Kalliokoski P, Pasanen P, Jantunen MJ, Nevalainen A. Laboratory studies on the relationship between fungal growth and atmospheric temperature and humidity. Environ Int. 1991;17:225–8.View ArticleGoogle Scholar
- Sedlbauer, K. (2001). Prediction of mould fungus formation on the surface of and inside building components. Germany: Ph.D. Thesis, Fraunhofer Institute for Building Physics.
- Abuku M, Jassen H, Roels S. Impact of wind-driven rain on historic brick wall buildings in a moderately cold and humid climate: numerical analyses of mould growth risk, indoor climate and energy consumption. Energy Build. 2009;41(1):101–10.View ArticleGoogle Scholar
- Brimblecombe P, Brimblecombe CT. Trends in insect catch at historic properties. J Cult Herit. 2015;16(2):127–33.View ArticleGoogle Scholar
- BSI. BS EN 16242:2012 Conservation of cultural heritage. Procedures and instruments for measuring humidity in the air and moisture exchanges between air and cultural property. London: BSI; 2012.Google Scholar
- Camuffo D. Microclimate for cultural heritage: conservation, restoration, and maintenance of indoor and outdoor monuments. 2nd ed. Amsterdam: Elsevier; 2014.Google Scholar
- Cardinale N, Ruggiero F. A case study on the environmental measures techniques for the conservation in the vernacular settlements in Southern Italy. Build Environ. 2002;37(4):405–14.View ArticleGoogle Scholar
- Ridout B. Timber decay in buildings: the conservation approach to treatment. London: E&FN Spon; 2000.Google Scholar